How much heating area can electric heating boilers generally provide? There is no specific answer to this question. The specific area should be decided according to the specific situation. Now Shandong Electric Heating Boiler Factory will give you a detailed introduction!
1. Insulation of buildings
If the building is well insulated, such as 300KW electromagnetic heating furnace can supply 3000 square meters, or even more than 3000 square meters; if the insulation situation is poor, the corresponding area will be reduced.
If it is in the high and cold area, the heating area supplied by the corresponding 300 KW will be reduced, and if it is in the general area, the heating area supplied will increase.
3. Water capacity of the system
System water capacity refers to the total amount of water contained in the HVAC system, including pipes and radiators. It can refer to the maximum system capacity corresponding to each type of heating furnace in the technical parameter table of electric heating boilers, so that the water capacity can not exceed the standard. If the area is suitable, but the installation of the heater is too much, it will cause too much water in the system, and the heating furnace will work for a long time without reaching the set backwater temperature, which consumes too much electricity and can not achieve good heating effect. Therefore, according to the actual situation, the water capacity should be estimated according to the specifications and models of customers'heating plates, so as to select the appropriate power of electric heating boilers.
The above content is provided by the small arrangement of electric heating boilers in Shandong Province. It does not represent the view of this website. If you have any questions, please leave a comment on our website: http://weishengz.com. Thank you very much for your love and support.